1.High-press CO2 Fire-extinguishing System Introduction:
The carbon dioxide is liquidized by high pressure and stored in cylinders, when spraying
the carbon dioxide is expending sharply and absorbing a large quantity of heat, thus to
reduce the temperature of the fire scene and dilute the oxygen level of the protected
zone so as to put the fire out. Carbon dioxide is a inert gas, which is inexpensive,
non-polluted, dissipated, and traceless. The carbon dioxide fire extinguishing system
is able to put gas fire out after the gas supply source is cut, and it is also able to put out
liquid fire, solid fire of fusible materials such as paraffin and asphalt, solid surface fire, deep-seated solid fire such as wincey, fabric, and paper, and electric fire, etc. The system is
applicable to libraries, archives, database, bulk storages of liquid, computer rooms,
communication rooms, generator rooms, substation rooms, oil immersion slots, mechanical mills, drying devices, and lacquer product lines. Note that carbon dioxide causes
asphyxiation and the system shall be used where no people are involved. If the system
takes effect in working places appropriate measures shall be taken to ensure safety.
The system puts out fires in a sealed room in a total flooding mode, it also works in a local
application mode to put out non deep-seated fire of protected objects where sealed rooms are not required. The local application mode uses special nozzles which allow the
extinguishing agent acts fully on combustion object directly, the system keeps supplying
extinguishing agent on the combustion object for a certain time and intensity in order to put out the fire.
2.CO2 Gas cylinder technical parameters:
Accessories: tank / valve/ internal siphon tube/flexible hose/gas check valve;
Tank size:1500* 267*5.7m(diameter*height*thickness);
Max working pressure(50ºC): 14.4MPa
Painting: red epoxy polysteter RAL3000/red coating polyster RAL3000;
Valve size:brass,thread: PZ39, hose thread: G5/8, release pressure:19 ±0.95;
Container valve is consisted of valve body, starter device, piston, relief device, etc.
Extinguishing agent spraying time:≤60s;
Protective area temperature:0ºC~50ºC
Spraying leavings of cylinder:≤3Kg/bottle
3.CO2 Fire suppression system accessories:
Fire control panel syotistem, smoke/heat/phc detector system, alarm system(fire bell, manual call,video alarm),equipment, cylinder, valve, selective valve, liquid
check valve,pressure switch, nozzle, pipe, ect.
4.CO2 System order instruction:
You are still in troubling get complex offer?? Hope you meet three following situation
Case 1. If client can supply drawing layout.we can make free design and make offer to you within 24hours, pls send us your drawing room layout.
Case 2. If client has equipment list ?? pls contact us, we can make free design and make offer to you within 24hours
Case 3. No any drawing layout, no equipment list, then give us your room size : length Xwidth X height and door information.
5.CO2 System packing information:
Use bubble bag packing the cylinder and accessories,then into wooden case,good protection.