Half Fixed Foam Extinguishing Equipment Foam Bladder Tank
water-insoluble liquid fire.It is widely used in municipal residential areas, factories and mines
enterprises, oil depot, chemical engineering department, heat treatment workshop, gas stations and other places, mainly made by the foam liquid storage tanks, spray gun,proportioning mixer, hose, and cart chassis, etc
|Model||rated working |
|mixing ratio||bubbling |
|25% abosorb |
|PY8/200||≥50 or ≥25|
|PY8/300||≥75 or ≥37.5|
|PY8/400||≥100 or ≥50|
|PY8/500||≥125 or ≥62.5|
Note: use foam liquid types: 1. The protein foam liquid fluorine protein foam liquid (2) using temperature range: 0 ºC ~ 55 ºC
- Use fire hose connect the water supply and pressure water inlet of equipment;
- Remove the spray gun and expand its fire hose;.
- Let the hose of spray gun and equipment outlet connect;
- Open the water supply;
- Armed with foam spray gun to fire extinguishing;
- Refill extinguishing agent:device after use,the user must purchase the same type of foam liquid supplement refill;Can use plastic tube suction or use funnel from charging liquid mouth into when refill;Tighten the filling cap after complete fill to prevent equipment moves foam liquid spills.
- Equipment should be kept in a place that cool, ventilated, convenient take and put.
- This tank of device material use corrosion resistance of glass fiber reinforced plastic material manufacturing. It is strictly prohibited to use hard ware damage knock, bump to leakage
- Stored for a long time not use this equipment, you should review annually foam liquid quality is bad or not. If discover metamorphism should be replaced on time;
- This equipment after each use,should be carefully cleaned and dry hose, after airing,then wrap on the reel, (suggest user should bring spare fire hose to backup, in case of sudden fire happen).
- In order to make the equipment for a long time in good state of fire prevention and foam liquid quality;Foam tank should be open to clean once every three years
- When water supply is the hydraulic pump or fire fighting water tanker, the pressure of water supply should be no greater than1.0 MPa.When purchasing equipment configuration should be bear work pressure biger than 1.0 MPa since a spoon fire hose.